Roofing Oak Park
Oak Park Roof Leak Repair
The Oak Park tiled roof had a severe leak located next to the chimney. There was a downspout attached next to the chimney wall that would overflow with water when it rained. The chimney flashings were installed incorrectly, making the overflow of water seep beneath the underlayment. Deterioration on the chimney included plywood damage, beam damage, and fascia damage. We replaced all of the rotten wood, added double layers of forty pound underlayment, and correctly re-installed the original tiles.
Damaged plywood on the right side of the chimney
Damaged beam next to the chimney
Deteriorated fascia board
Installing brand new plywood
Installing new beams and fascia
Oak Park Tile Roofing
In this instance, the home’s tiled roof had quite a few leaks. These were all caused by tiles that were missing and clogged drainage from fallen tree leaves and debris. After finding damaged plywood and fascia board at the front edge of the roof, we decided to replace all the damaged wood. We added double layers of forty pound underlayment and re-installed the original tiles. We finished by adding tile pans at the front edge of the roof to improve drainage and prevent clogging.
The clogged valley and missing tiles that caused the leak
Severe plywood, fascia, and rafter damage from the roof leak
Replacing and installing plywood and fascia
Before and after the repair